We're aware of an outage on Grantham node 69, we're currently working on repairing this.
Two cooling fans failed at the same time and the system has shut down to prevent damage.
Due to COVID-19 our technicians are working remotely, a member of the team has been dispatched and is now on site.
We expect the fans to be replaced and the node to be back online within 15 minutes.
17:10pm GMT - Machine's failed cooling fans have been replaced and the machine is now back online.